Before disinfecting the surface water is pre-filtered by means of a
floating filter and a inside 60m
filter to remove dirt and dissolved particles. Both filters can be washed
up or if necessary easily replaced.
Part of the incoming surface water is sent through the
M incorporated into the Reactor that automatically fills up the anolyte
container. From that container anolyte is dosed into the surface water at
ratio needed for disinfecting (dosing regimes 1 : 800, 1 : 1000). The
dosing regime is controlled by ORP-meter to ensure that disinfecting is
Drinking water on site and on demand
disinfecting the treated surface water is filtered by a (active-carbon)
filter to improve and ensure good taste of the disinfected water.
The input water at the
is controlled by a input valve, pressure reducer and flow controller.
Saturated NaCl solution is automatically dosed in to the input water by a
peristaltic pump in order to obtain an accurate saline solution. The salt
container, as well as the Anolyte- container are located at the bottom of
unit, to enable manual tapping of Anolyte.
Ready to go wherever clear water is needed
on the lake side